FlowCon works with
Three Flushing Strategies:
1: Flush with the Regulation Element present:
If a complete valve is installed prior to flushing, then a strainer (with basket) should also be installed upstream. The strainer basket should be examined continuously throughout the entire process and cleaned if necessary. Both forward and back flushing are generally accepted (please refer to product literature for advice).
2: Flush without the Regulation Element present:
The unique removableinsert-based solution offered by FlowCon allows flushing prior to installing the regulation element. Install valve housing with a flushing cap and perform proper system flushing, (which can be full force forward or backward). Then the commissioning team sets design flow on the insert and installs it into the housing. Such procedure will greatly reduce time spend on cleaning baskets, as centrally located strainers may be used for dirt collection. This two-step procedure can furthermore be used as procedure validation, by requesting a flushing and water quality report prior to installing the insert.
3: Flush through Flushing By-Pass Unit:
Using a FlowCon by-pass solution will accept forward and back flushing, as well as isolation of the FCU to perform system flushing. This solution will also offer major benefits during maintenance and service periods.
FlowCon offers a wide range of insert types to suit any application in a HVAC system. FlowCon insert solution is a benefit during selection, installation, flushing, commissioning and maintenance.